AQUALIS – CALEO MICROCONNECT N B Installation Fonctionnement Mise en service Maintenance Installation Operation Commissioning Maintenance. Aqualis Caleo. 60H. 60HT. 70HT. Heating capacity *. kW. Power input *. kW. COP. Refrigerant fluid RC – Load. CIA. T CALEO. 10 – NA E. Instruction manual . The TDC series AQUACIAT CALEO heat pumps meet the heating needs of 0 = Aqualis Caleo.
|Published (Last):||15 May 2018|
|PDF File Size:||17.36 Mb|
|ePub File Size:||7.5 Mb|
|Price:||Free* [*Free Regsitration Required]|
The diameters of the tubes are not necessarily the same as those of the unit.
If you do not have a torque wrench, tighten them until they are snug then tighten a further quarter turn. A 3 bar safety valve must be placed on the water loop. Please read before installation. These instructions covers the installation of replacement coil kit into. Anti-vibration mounts 4 mounting points M8 screws dia. Installation Fonctionnement Mise en service Maintenance. Compressor The calek is fastened to the platform by four 8 mm dia.
HERZ-Thermal Actuators Data SheetIssue Dimensions in mm 1 00 1 01 1 18 1 80 1 81 1 80 1 81 1 00 1 00 1 11 1 10 1 23 1 A two More information. With the thought of material improvement always in mind, CIAT reserves the right, without notice, to proceed with any technical modification.
The complete table of settings is given on the following page. It may be necessary to use them when starting the unit or when turning it ccaleo for extended periods of time. The recommendations and instructions given in the maintenance instructions and the special instructions on the labels must be followed. Terminal display when the outdoor temperature is less than P9 and only the boiler is authorised.
Remove the top as shown in Figure 1 and make a connection to terminal block J1 on the PSU aqaulis the one with the contactor.
NAN – CIAT – PDF Catalogs | Technical Documentation
Always mix the correct amounts of water, antifreeze xqualis corrosion inhibitor in a container before adding them to the system Procedure 1- Rinse and drain the system Always flush the system completely and blow it out to remove any remaining water.
Check the glycol content if used. Maximum water return for boiler backup: Each comes equipped as standard with: Hoses must be used to connect the water pipes to limit as far as possible the vibrations transmitted to the building.
English The differential water pressure switch is a safety component. Check the water filters for dirt.
Automatic, Comfort, Energy Saving, and Frost. Installation Fonctionnement Mise en service Maintenance”. Although it is rain resistant, it may be installed under a shelter with adequate ventilation on all four sides. Frost protection Indicator 2: Protecting your system To protect your heating system and avoid all risks of it freezing should it be intentionally or accidentally turned off, we strongly advise that you: Frost protection Indicator 2: Make sure the terminals are securely tightened.
April This manual supersedes. The complete table of settings is given on the following page. It may be necessary to use them when starting the unit or when turning it off for extended periods of time. If water installation capacity superior to the values indicated in the technical characteristics table chap 7.
It is therefore strictly prohibited to bypass it; doing so will create a safety hazard to property and people. Walls can increase noise levels considerably and reflect noise in various directions. The valve does not need to be separated from the heater by a shut-off valve.
AWG 16 to 28; or 0. Adjusting setting P6 P6 Auxiliary configuration Bypass type by opening of contact on terminal block J2 – terminals 4 and 5 0 No auxiliary units Heat pump turned off 1 Electric auxiliary units Only electric auxiliary units turned off 2 Electric auxiliary units Heat pump and electric auxiliary units turned off 3 Boiler auxiliary Heat pump turned off and boiler turned on e.
Protect your indoor water circuit with a mix of water, antifreeze and corrosion inhibitor and, possibly, a biocide. These instructions should More information.
Heating provided primarily by the heat pump auxiliaries may however be used The maximum water return setpoint is limited to 40 C Heating provided by auxiliaries. The fault type appears on the terminal LCD.
Heating mode The compressor will start up after a few seconds. If your system is fitted with an optional electric heater, install the valve near it. With the unit running, check it thoroughly for any abnormal visual signs or noises.
Connect your contact between these two terminals. Randell Jackson 1 years ago Cwleo To do so, simply loosen the nut measure on the bottom of the pressure switch approx.
Air/water heat pump – AQUALIS R series – CIAT
English Fig 1 1 Remove the middle screw rear of unit 2 Detach both ends as shown in picture 3 Remove of the top by sliding it toward the rear D e u t s ch – The characteristics of the mains supply aquallis be identical to those on the data plate. Protect from prevailing winds. Then check for any leaks. It is your responsibility to protect the unit from mains voltage spikes and voltage spikes caused by lightning.